Preconfiguration "PmModbusMr - Papouch PAPAGO 2x measurement (Modbus TCP/IP) - Communication set with data and panel"
Communication by the Modbus TCP/IP
protocol with PAPAGO
See also Communication with meters by the Papouch company (Czechia)
The valid TCP-IP
address must be set for the device according to the corresponding network environment. The configuration is described in the user manual supplied by the manufacturer.
This preconfiguration can be activated when creating a new object (e.g. by "New object ..."
in the local object menu or after pressing the Insert
key after selecting the object) and is included in the group: "/ Communication / Modbus"
This preconfiguration can be created in the object: PmaFolder
- The preconfiguration is created including the panel (object of the PmaPanel
type) is functional also a Web panel
- The panel is used for communication testing and it is not essential for the functionality.
In the PmaComm
object named "Comm
" the communication parameters are set (Network address
object named "data
" includes a "Parameters
" tab where Special Parameters
are defined (see PmModbusMr - Driver for communication by the Modbus Master protocol
). On the "Data
" tab, the items are imported by data extension of items defined in the PmaData
object (see ExtComm
). Each Data
corresponds to the selected device type by its structure and name.
These configurators can be set before the preconfiguration is created:
|The name of created object||Name of the object created in the tree of Pma objects. The maximum name length is 30 characters. This is a system name, so it must contain only alphanumeric and must not contain any diacritics, empty string, spaces and the first character must not be a number.
|Meter type||2x measurement according to the device type
2TH - 2x temperature and humidity meter
2PT - 2x thermometer for Pt100/1000
2TC - 2x thermometer for K-type thermocouple
|Network address||Network address to which the communication will be connected. The address can be entered by both IP address (e.g. 192.168.0.15) or by name (e.g. server11).
Macro expression can be used for input (it is evaluated after starting the application).
After the preconfiguration is created, the "PmaComm > Setting the parameters of the Ethernet-client > Network address" configurator will be set to this value.
|Communication refresh rate [ms]||The period in milliseconds to be used for reading the current data by the PROMOTIC application.
After the preconfiguration is created, the "PmaCommGroup > Parameters > Communication refresh rate [ms]" configurator will be set to this value.
|Panel title||Displayed in the panel header|