Now you can proceed to the final step of the trend configuration - definition of variablas that are to be trended:
- Go to the Data
page in the "BoilerPlant/Boiler1/Data
- Select the variable: "Temperature". Open the configuration window of this variable (by the Edit button or doubleclick)
The Trend data extension
configuration window opens now:
: Enter temp1
here. This way you have also defined the column name in the table where the variable is going to be saved.
: Name of the variable that will be displayed for the user in running application. It may contain diacritics, spaces, etc. Enter "Temperature of boiler no.1
: The physical unit of the value, enter °C
here. (press Alt + 0176 to get the degree character on English keyboard).
: You can press the colored button in order to choose the color of the variable to be used in the chart.
Leave the other items displayed in this window unaltered.
Confirm the modifications. You have just defined that the "Temperature"
variable will be trended with the period of one second. You can now use similar procedure in order to trend the "Power
" variable. After application launch, you can check the Data
folder located in the application folder. You should find a trend
folder there containing data file(s) of the *.dbf
type. These files can be easily opened (viewed) in MS Excel
After following the procedure described above, you have created the application that saves the values of "Temperature"
variables into a database table of the *.dbf
type every second. In the following chapter you will learn how to display the saved data.