Preconfiguration "PmSNMP - Papouch up to 32 temperature and humidity sensors TME multi (radio) (Communication by SNMP protocol) - Communication set with data and panel"
Communication by the Communication by SNMP protocol
protocol with sensors via TME multi
Communication driver configuration PmSNMP - Driver for communication via the SNMP protocol
See also Communication with Papouch meters (Czech republic)
The valid TCP-IP
address must be set for the device according to the corresponding network environment. The configuration is described in the user manual suppiled by the manufacturer.
This preconfiguration can be activated when creating a new object (e.g. by "New object"
in the local object menu or by pressing the Insert
key after selecting the object) and is included in the group: " / Communication / SNMP communication protocol"
This preconfiguration can be used with the objects: PmFolder or PmRoot.
- The preconfiguration is created including the panel (PmPanel
object) functionality as a Web panel
- The panel is used for communication testing and it is not essential for the functionality.
In the PmComm
object named Comm
the communication parameters are set (Network address
The PmCommData object named data includes a Parameters page where Special Parameters are defined (see PmSNMP - Driver for communication via the SNMP protocol). On the Data page, the items are imported by the data extensions of the items defined in the PmData object (see ExtComm). Each Data corresponds to the selected device type by its structure and name.
These configurators can be set before the preconfiguration is created:
|The name of created object||Name of the object created in the application object tree. This is a system name and must not contain empty string, diacritics, spaces and the first character must not be a number.|
|Network address||Network address to which the communication will be connected. The address can be entered by both IP address (e.g. 192.168.0.15) or by name (e.g. server11).|
Macro expression can be used for input (it is evaluated while the application is launching). After this preconfiguration is created, the configurator is se to: PmComm > Settings of the Ethernet parameters > Network address
|Communication refresh rate [ms]||The time period in milliseconds to be used for reading the data by the PROMOTIC application. After this preconfiguration is created, the configurator is se to: PmCommData > Parameters > Communication refresh rate [ms]|
|Panel title||Displayed in the panel header|