Communication driver configuration PmModbusMr - Driver for communication by Modbus Master protocol
The West 6100+
device is designed for temperature measurement and regulation. The PROMOTIC application communicates with the device by the PmModbusMr - Driver for communication by Modbus Master protocol
See also Communication with meters and regulators by the West Instruments company.
The device can be connected to the PC using the terminals no 11 and 12 (RS485
) via the RS485/RS232
converter to the serial port of the computer (RS232
). The connection is described in the manual suppiled by the manufacturer of the device.
This preconfiguration can be activated when creating a new object (e.g. by "New object"
in the local object menu or by pressing the Insert
key after selecting the object) and is included in the group: " / Communications / Modbus protocol"
This preconfiguration can be used with the objects: PmFolder or PmRoot.
- The preconfiguration is created including the panel (PmPanel
object) functionality as a WEB panel
- The panel is used for communication testing and it is not essential for the functionality.
The communication parameters (Serial port
, speed [Bd]
....) are defined in the PmComm
object named Comm
. The PmCommData
object named data
includes a Parameters
page where Special Parameters
(See: PmModbusMr - Driver for communication by Modbus Master protocol
) are defined. On the Data
page, the items are imported by the data extensions of the items defined in the PmData
object (See: ExtComm
). Each Data
corresponds to the selected device type by its structure and name according to the description provided bythe manufacturer.
object named Trend
contains the setting in the configurator Storage type
, that defines saving the trend values into Database dBase backups
. The data items for the PmTrend
object are defined in the PmData
object using the ExtTrend
object contains ActiveX trend viewer TrendsView
. There are also PmiButton
graphic items for entering values and for controlling the viewer. The items PmiRasterImage
indicate the current status by colours and items PmiText
contain description texts or values displaying the current status of the measurement.
These configurators can be set before the preconfiguration is created:
|The name of created object||Name of the object created in the application object tree. This is a system name and must not contain empty string, diacritics, spaces and the first character must not be a number.|
|Permissions||On this page permissions of the object are defined. See Description of the page Permissions.|
|Serial port||Selection of the communication serial port.|
After this preconfiguration is created, the configurator is se to: PmComm > Settings of the serial link parameters > Serial port.
- The object is not connected to any port at the start of the application and the serial port can be selected dynamically by the algorithm (by the PmComm.OpenPort
- The object is meant for the data transfer over the dialed phone line (over the PmModem
object). The serial port is assigned by the PmModem.SetPmComm
method or by the PmComm object
configurator of the PmModem
- The specified serial port is opened at the start of the application. This port must be correctly configured and accessible in the OS Windows
(no one can use it).
For serial link each PmComm object must have defined another communication port. For example, when one PmComm object communicates through COM1, then next PmComm object can communicate for example through COM2 (COM3,..) but it mustn't communicate through COM1.
|Baud rate||Selection of the baud rate (bps, bit per second). |
This configurator sets the initial value of the property BaudRate.
After this preconfiguration is created, the configurator is se to: PmComm > Settings of the serial link parameters > Baud rate
|Communication refresh rate [ms]||The time period in milliseconds to be used for reading the data by the PROMOTIC application. After this preconfiguration is created, the configurator is se to: PmCommData > Parameters > Communication refresh rate [ms]|
|Autosave period [s]||The period in seconds. Always after this time perios is up, the Run method is called internally, which first calls the onAddRecord event and then saves all current values from the Data page. |
After this preconfiguration is created, the configurator is se to: PmTrend > Trend > Autosave period [s].